Match your roof line to one of these below to get started so you know the path to run your cable and calculate footage of product you need.
Grounding Techniques and examples below with ground rods or ground plates.
Aluminum Grounding Detail:
Order # M3 Bi-Metal Splicer
All buildings must have two groundings as widely separated as possible, preferably at diagonally opposite corners if perimeter, distance around, is 250 feet or less.
If building perimeter is between 250 feet and 350 feet, then three groundings are required. If between 350 feet and 450 feet, then four groundings, etc.
Lightning Protection Systems shall be applied to metal covered buildings in like manner as on buildings without metal coverings.
Cables shall be free of sharp turns and "u" or "v" pockets. Cables shall maintain a horizontal or downward course
Illustration of cable going over eaves and gutter spouts. Gentle curve and loop.